The IR Extension is designed to control up to 8 IR modules and is used to control IR capable devices like TVs, AV receivers, projectors, air conditioners, etc.
The Loxone IR Extension and the IR Modules are no longer available. Use the IR Control Air instead.
Table of Contents
The IR Extension is installed on a DIN rail in a suitable enclosure.
Connect the power supply, Link communication to the Miniserver and the data lines connecting the IR Modules.
The IR modules are connected via RJ45 plugs and daisy-chained as shown in the diagram.
A CAT5/6/7 cable is used for wiring, the max. cable length is 500m.
The last IR module must be terminated by setting the jumper to pin 2/3.
2 IR transmitters can be connected to each IR module (3.5 mm connector). If only one transmitter is connected, it must be plugged into the left socket.
The IR receiver is integrated in the IR module.
The Extension starts after switching on the power supply, and the status LED will flash orange after a short time when the connection to the Miniserver is established.
Adding an IR Module↑
To search for IR Modules, first click on the IR Extension in Loxone Config, and then activate IR Device Search.
The search results at the bottom of the Loxone Config, will list all connected IR Modules.
Now select a Module, enter a name and then click on Create device.
To apply the changes, save the program in the Miniserver.
Now the added Modules are ready for use and available in Loxone Config.
Additional steps to create IR sensors (receiver) and actuators (transmitter), as well as for creating and learning remote controls is described at IR Control Air.
|Online Status IR Extension||Digital|
|Serial number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Maximum cable length (m)||Maximum cable length in meters to the last IR-module.||-|
|Monitor online status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The installation requires a suitable enclosure to ensure protection against contact, water and dust.
The device must not be used as part of safety-critical systems.