The Loxone Touch Pure Tree features five touch points on a glass surface to control the most important functions of a room. When a button is touched, an audible click confirms the action.
The large center touch zone is ideal for controlling the lighting, while the corner zones are suitable for controlling music and shading. It is based on the Loxone switch standard. The buttons can also be freely used for other applications.
It also features a controllable orientation light and the integrated sensor measures temperature and relative humidity.
Please note that there is a certain delay when measuring humidity due to the housing. The Room Climate Sensor is better suited for a fast detection of changes in humidity.
Table of Contents
Install the mounting frame at the desired location.
Connect the power supply (orange/white terminal) and Tree communication wires (green/white terminals). Shortly after power-up, the status LED will blink orange if the wiring is correct (connection to Tree Extension and Miniserver is established).
Mount the device by snapping it onto the mounting frame.
|T5||Combined input for the 5 touch points according to the Loxone Switch Standard.||-||∞|
|Temperature||Provides the air temperature.||°||-40...125|
|Humidity||Provides the air humidity.||%||0...100|
|Orientation light||Digital output to control the orientation light.||0/1|
|Online Status Touch Pure Tree||Digital||0/1|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-|
|Serial Number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Device type||Tree device type||-|
|Show Button 1||Show individual button||-|
|Show Button 2||Show individual button||-|
|Show Button 3||Show individual button||-|
|Show Button 4||Show individual button||-|
|Show Button 5||Show individual button||-|
|Audible acknowledgement||Audible acknowledgement on button press||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.