The LED Spot RGBW Tree is a recessed LED spot with warm white and coloured light for supply with 24VDC. The connection to the Miniserver is via Loxone Tree technology.
Table of Contents
- Tree Communication and Voltage Drop
- Inputs, Outputs, Properties
- Safety Instructions
Switch off the supply voltage before installation.
Connect the power supply (orange/white wire) and Tree communication wires (green/white wire).
Flip the spring clips back and snap the spotlight into the mounting hole. Make sure that no wires are jammed.
Tree Communication and Voltage Drop↑
If the current flow on the GND line results in a voltage drop too high, this potential difference also affects the tree communication.
To solve this problem, split consumers of higher power over longer distances to several supply lines, or use a supply line with a higher cross-section, or a power supply close to the consumers.
For existing installations, doubling the cross-section of the GND line is often sufficient to eliminate the potential difference.
|Smart actuator RGBW||Smart actuator||∞|
|Online Status LED Spot RGBW Tree Gen. 1||Digital||0/1|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-|
|Serial Number||Specifies the serial number of the device.
For Extensions: Enter 'Auto' to automatically pair an extension with unknown serial number.
This can only be used if there is only one Extension of the same type.
Save into the Miniserver, in order to pair the Extension.
Afterwards the program must be loaded from the Miniserver to transfer the actual serial number of the Extension into the program.
|Device type||Tree device type||-|
|Actuator Type||Use device with Standard Actuator(s) or Smart Actuator(s)
Smart Actuators support dynamic fade times and can only be used with the Lighting Controller.
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.