- Suitable for a voltage of 85 – 265VAC
- Max. switching capacity: 16A
- Integrated measurement of energy (kWh), power (kW) and temperature (-20 to 50°C)
- Frequency: 868MHz
- Power consumption: <500mW
- Protection: IP20
- Safety shutdown: If the CPU temperature increases over 92°C, all the relay is turned off. Once the temperature drops below 77°C, the relay is turned on. The CPU temperature is updated on startup and if there is a temperature change of more than 5°C.
TRANSFER OF ENERGY AND POWER:
Every 5 minutes information about the energy and power is sent to the Miniserver.
If a 5% change in the data occurs this update is sent immediately to the Miniserver.
TRANSMISSION OF THE TEMPERATURE:
Every 5 minutes the temperature is sent to the Miniserver.
Contains FCC ID: COR-ZWIR4512AC1.
This device complies with part 15 of the FCC Rules. Operation
is subject to the following two conditions:
(1) This device may not cause harmful interference, and
(2) This device must accept any interference received, including interference that may
cause undesired operation.
Used in: USA, Turkmenistan, Trinidad, Tobago, Thailand, Thaiti, Saudi Arabia, Puerto Rico, Peru, Paraguay, Panama, Okinawa, Niger, Netherlands Antilles, Montserrat, Micronesia, Liberia, Lebanon, Colombia, Canada, Cayman Islands, Virgin Islands, Japan, Jamaica, Honduras, Haiti, Guyana, Guatemala, Guam, Ecuador, Dominican Republic, Costa Rica, Brazil, Bermuda, Barbados, Aruba, Barbuda, Venezuela.
Used in: United Kingdom, Bahrain, Bangladesh, Belize, Bhutan, Botswana, Brunei, Dominica, El Salvador, Falkland Islands, Gambia, Guatemala, Guyana, Hong Kong, Ireland, Isle of Man, Yemen, Cambodia, Channel Islands, Qatar, Kenya, Kuwait, Lebanon, Macau , Malawi, Malaysia, Maledicen, Malta, Mauritius, Myanmar, Nigeria, Oman, Zambia, Seychelles, Tanzania, Cyprus, Singapore.
Used in: Afghanistan, Algeria, Andorra, Bosnia and Herzegovina, Bulgaria, Germany, Estonia, Finland, Greece, Indonesia, Iceland, Italy / San Marino / Vatican City, Korea, Croatia, Latvia, Lithuania, Luxembourg, Macedonia, Montenegro, Moldova, Netherlands, Norway , Austria, Portugal, Romania, Russia, Sweden, Serbia, Slovenia, Spain, South Korea, Syria, Turkey, Ukraine, Hungary.
Used in: France, Belgium, Monaco, Czech Republic, Slovakia, Tunisia, many former French colonies.
Used in: Switzerland, Liechtenstein, Maldives, Madagascar, Rwanda, Ethiopia, El Salvador, Jordan.
SETUP IN LOXONE CONFIG
Plug in your Smart Socket and then press and hold the learn button for 5 seconds within 10 seconds of powering on the Smart Socket – see the picture below. Once the device is in the learning mode, the Status LED will flash alternately red-green-yellow.
|Flashing orange||Is not yet paired with the Air Base or no connection is possible|
|Flashes green for 3 secs||After being restarted a connection to the Air Base was successful|
|No LED||Device operational|
|Flashing red-green-yellow||Device is in learn mode|
The LED may also be manually controlled in Loxone Config. In the peripheral tree you will find the output “Smart Socket Air LED”. The 3 different colours can be set:
0 = Off
1 = Green
2 = Orange
3 = Red
You can connect the energy and power inputs of the Smart Socket Air to the Utility meter function block to display things like Today’s usage, This Month’s usage etc. You can also simply tick ‘Use’ on the inputs in the properties to show the current energy and power readings.