The KNX Extension is designed to integrate devices with KNX interface.
In Loxone Config KNX sensors and actuators can be paired and configured, and then used in programming.
To address and configure the KNX devices the ETS software by the KNX Association and an external KNX gateway are required.
Table of Contents
The KNX Extension is installed on a DIN rail in a suitable enclosure.
Connect the power supply, Link communication to the Miniserver and the KNX data lines.
A separate KNX power supply is required to power the KNX bus.
The Extension starts after switching on the power supply, and the status LED will flash orange after a short time when the connection to the Miniserver is established.
To integrate KNX devices, the corresponding sensors and actuators must be created or paired in Loxone Config:
For additional information please visit the documentation on our website:
|Online Status KNX Extension||Digital|
|No KNX Connection||Digital|
|KNX Sending not possible||Digital|
|Serial number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Monitor online status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-|
|Own EIB Address||The EIB line's own physical address (x.x.x).
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The installation requires a suitable enclosure to ensure protection against contact, water and dust.
The device must not be used as part of safety-critical systems.