|Power Supply||10…28VDC PELV|
|Power Consumption||max. 75mW|
|Total Power Loss||max. 150mW|
|Ambient Temperature||-25…55°C / -13…131°F|
|Humidity||95% r.H (non-condensing)|
|Maintenance||This device is free of maintenance and must only be cleaned with a dry cloth.|
|Dimensions||35.5 x 88 x 57 mm (2 TE)|
|Cable distance to KNX /|
EIB Power Supply
|Cable distance to first KNX /|
|Total Cable Length KNX / EIB||max. 1000m|
|KNX / EIB – actuators/sensors||Up to 500 group addresses|
Install the unit in a suitable distribution box where it is protected from water, dirt and mechanical damage.
Connect the power supply (orange/white), the Loxone Link (blue/white) and the KNX bus (red/grey).
After switching on the power supply the device starts, the status LED flashes orange after a short time when connected to the Miniserver.