The Extension features 8 dry contact relay outputs, 12 digital inputs, 4 analog 0-10V inputs and 4 analog 0-10V outputs.
The digital inputs can also be used as frequency counters, to connect for example S0 meters or wind sensors that transmit pulses.
The analog inputs can also be used as digital inputs.
Table of Contents
The Extension is installed on a DIN rail in a suitable enclosure.
Connect the power supply and Link communication to the Miniserver.
Connect the loads to the relay terminals. You will find various connection examples below.
|Many electronic loads such as ballasts, power supplies, LED drivers and high voltage LED lamps can draw high inrush currents of over 20A. Use inrush current limiters or a coupling relay with the necessary current rating for such cases.|
If the devices are connected to different power supplies, it is essential that the GNDs are interconnected.
The Extension starts after switching on the power supply, and the status LED will flash orange after a short time when the connection to the Miniserver is established.
|Actuator (Relay) 1||Digital||-|
|Actuator (Relay) 2||Digital||-|
|Actuator (Relay) 3||Digital||-|
|Actuator (Relay) 4||Digital||-|
|Actuator (Relay) 5||Digital||-|
|Actuator (Relay) 6||Digital||-|
|Actuator (Relay) 7||Digital||-|
|Actuator (Relay) 8||Digital||-|
|Online Status Extension||Digital||-|
|Temperature Shutdown||If the CPU temperature reaches a critical point, the outputs of the device are switched off. This can be due to short-circuits, overloaded switching loads or too high an ambient temperature.||Digital||-|
|Serial number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Monitor online status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The installation requires a suitable enclosure to ensure protection against contact, water and dust.
The device must not be used as part of safety-critical systems.