The DI Extension features 20 digital inputs.
The inputs can also be used as frequency counters, to connect for example S0 meters or wind sensors that transmit pulses.
Table of Contents
The DI Extension is installed on a DIN rail in a suitable enclosure.
Connect the power supply and Link communication to the Miniserver.
You can connect push buttons to the digital inputs, for example. When using the inputs as frequency counters, wind sensors or S0 meters can also be connected.
If the devices are connected to different power supplies, it is essential that the GNDs are interconnected.
The Extension starts after switching on the power supply, and the status LED will flash orange after a short time when the connection to the Miniserver is established.
|Online Status DI Extension||Digital|
|Serial Number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Monitor Online Status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The installation requires a suitable enclosure to ensure protection against contact, water and dust.
The device must not be used as part of safety-critical systems.