The Loxone Water Sensor Air is a wireless sensor with two contacts on the bottom. The sensor activates when the contacts come into contact with a conductive liquid. This allows monitoring of indoor water intrusion or leakage.
Table of Contents
- Battery Replacement
- Inputs, Outputs, Properties
- Safety Instructions
The sensor triggers when the two contacts on the bottom come into contact with water.
|If the sensor was submerged in water, it will no longer operate and must be replaced by a new sensor. When installing the sensor, make sure that it is not subjected to water in everyday use, for example when cleaning the floor.|
|When mounted to metallic surfaces, the range may be significantly reduced.|
In delivery state, pairing mode will be active after inserting the battery. This is indicated by the status LED flashing red/green/orange.
Then follow the pairing procedure
To activate the pairing mode manually, hold down the pairing button for at least 5 seconds after inserting the battery. The pairing button is located on the top of the device.
Use the white button as a slider to eject the battery to the side. Then insert a new CR2032 lithium battery. Make sure that the battery is completely inserted into the device and that the button can be operated correctly.
|Input 1||To use the pairing button as Input||0/1|
|Contact||Input is active when water is detected||0/1|
|Online Status Water Sensor Air||Digital||0/1|
|Battery level||Provides the current battery level.||%||0...100|
|Battery low||Indicates low battery, battery needs to be replaced.||-||0/1|
|Monitor Online Status||You will be notified via System Status or Could Mailer if the device is no longer available or offline.
As this device and it's functionality are critical to safety, it is not possible to disable this setting for this device.
|Serial Number||Serial number of the Air device||-|
|Device type||Air device type||-|
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.