The Loxone Wallbox is a charging station which enables dynamic charging from 1.38kW to 11kW for electric vehicles.
With the robust Tree interface, the device is integrated into the Loxone system and provides all the freedom for energy management.
To record the electrical energy, an energy meter can be easily mounted on the integrated DIN-rail and connected to the Modbus interface in the device.
Optionally, products like the NFC Code Touch, Touch Pure Flex,... can be mounted directly on the device to set your charging mode or execute any other control.
Table of Contents
- LED Status
- Charging Cable
- Inputs, Outputs, Properties
- Safety Instructions
After mounting, the supply voltage (mains voltage and 24V) is switched on, the Wallbox flashes orange after a short time if the connection to the Miniserver is successful and is ready for pairing.
The Loxone Wallbox is programmed and set up using the Wallbox function block in Loxone Config:
|Device has just been paired or has restarted and is now online.|
|Connection to Miniserver is okay, but the device has not been paired.|
|Device cannot connect to the Miniserver via the Tree interface.|
|Device was selected in Loxone Config and is identifying.|
If it is necessary to replace the charging cable, this must be installed and tested by a specialist in accordance with national regulations.
For this purpose, a charging cable with the same properties must be used; this may also be shorter or longer (max. 7.5 meters).
Extending the charging cable in any other way is not permitted.
|API Connector||Intelligent API based connector.
|Charging error||Reports a charging error.||-||0/1|
|Fault current||Reports a fault current.||-||0/1|
|Online Status Wallbox Tree||Digital||0/1|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-|
|Serial Number||Specifies the serial number of the device.
For Extensions: Enter 'Auto' to automatically pair an extension with unknown serial number.
This can only be used if there is only one Extension of the same type.
Save into the Miniserver, in order to pair the Extension.
Afterwards the program must be loaded from the Miniserver to transfer the actual serial number of the Extension into the program.
|Device type||Tree device type||-|
Installation must be carried out by a qualified electrician in accordance with the applicable regulations.