The GEIGER SOLIDline Air is a tubular motor for roller shutters and awnings, controlled via Loxone Air technology.
Table of Contents
- Setting the end limits
- Inputs, Outputs, Properties
- Safety Instructions
Follow the instructions to install the SOLIDLine Air motor:
|Please ensure that the power cable plug is fully inserted into the tubular motor, as shown in the following image:|
In delivery state, pairing mode will be active after the power supply has been established. This is indicated by an audible "clack-clack" (short up/down movement).
To activate the pairing mode manually, switch off the power for 10 seconds, then switch it back on. If no connection to a Miniserver can be established for two minutes, then pairing mode is activated for 30 minutes.
Setting the end limits↑
After pairing the device, it will be available in the periphery of Loxone Config. Drag the SOLIDLine Air from the periphery tree onto the program page and save the program into the Miniserver, then set the end positions.
The direction of rotation depends on the installation position. The shading should be in a middle position when programming the end limits so that it can move freely in both directions.
To set the end limits, activate the service mode in the App. Then use the buttons in the app to adjust the position of your shading. Once the end position has been reached, save it by clinking "Save end position".
The end limits are independent of each other and can be set with or without stoppers. The motor confirms the setting of the lower limit with "clack-clack" and the upper limit with "clack-clack-clack", which also indicates the end of the setting procedure. The time between setting the lower and upper limit must not exceed 2 minutes, otherwise the previous or factory settings will be restored, which the motor would indicate with a "clack-clack-clack-clack-clack-clack".
Once the end limits are programmed, you can exit the service mode. If the limits need to be readjusted, briefly disconnect the motor from power. The service mode can then be activated within the first 30 minutes of re-establishing power to the motor and the end limits can be set again. No end positions are set in delivery state.
|Online Status GEIGER SOLIDline Air||Digital||-|
|Temperature Shutdown||If the CPU temperature reaches a critical point, the outputs of the device are switched off. This can be due to short-circuits, overloaded switching loads or too high an ambient temperature.||Digital||-|
|Monitor Online Status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-|
|Disable Routing Functionality||Disable router functionality of this Air device.
Loxone Air is based on mesh technology. Any air device connected to the power supply can route packets from other Air devices, thus extending the range and stability of the overall system.
In large systems with a large number of air devices in a confined space, the communication between the air devices can lead to a very high radio channel utilization. A reliable accessibility of the air devices can not be guaranteed. Disabling router functionality on individual Air devices can help.
Do not disable this function recklessly as this may affect the range and stability of the system.
|Air serial number||Serial number of the Air device||-|
|Device type||Air device type||-|
|Application||Sets what the GEIGER SOLIDline Air is used for.||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The device must not be used as part of safety-critical systems.
Please note the safety instructions in the installation and operating manual.