The Loxone Touch Tree features five touch points to control the most important functions of a room. When a button is touched, an audible click confirms the action. An integrated sensor measures temperature and relative humidity.
The large centre touch zone is ideal for controlling the lighting, while the corner zones are suitable for controlling music and shading. It is based on the Loxone switch standard. The buttons can also be freely used for other applications.
Please note that there is a certain delay when measuring humidity due to the housing. The Room Climate Sensor is better suited for a fast detection of changes in humidity.
Table of Contents
Install the device on a suitable installation box.
Connect the power supply (orange/white terminal) and Tree communication wires (green/white terminals).
Touch Tree US:
Finally, secure the device by snapping it onto the mounting frame or screwing it onto the frame of the installation box, depending on the model.
Shortly after power-up, the status LED on the back of the device will blink orange if the wiring is correct (connection to Tree Extension and Miniserver is established).
The maximum duration of a long click is limited to 15 seconds.
|Online Status Touch Tree||Digital|
|Monitor online status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-|
|Serial number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Device type||Tree device type||-|
|Show Button 1||Show individual button||-|
|Show Button 2||Show individual button||-|
|Show Button 3||Show individual button||-|
|Show Button 4||Show individual button||-|
|Show Button 5||Show individual button||-|
|Audible acknowledgement||Audible acknowledgement on button press||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The installation requires a suitable enclosure to ensure protection against contact, water and dust.
The device must not be used as part of safety-critical systems.