The Loxone Smoke Detector Air is a photo-electric smoke detector. When smoke is detected, the device emits a loud alarm signal. The alarm is also transmitted to the Miniserver. This allows for further steps to be initiated via programming.
Table of Contents
- Operating and alarm signals
- Inputs, Outputs, Properties
- Safety Instructions
The correct amount and position of smoke detectors is essential to achieve effective protection. Local code and regulations must be observed.
Start by mounting the base plate. Then insert the 9V battery and plug it in. Place the detector on the base plate and lock the device with a short clockwise turn. (This is only possible when the battery is inserted)
In delivery state, pairing mode will be active after inserting the battery. This is indicated by the status LED (light guiding key) flashing red every second
To activate the pairing mode manually, hold down the pairing button for at least 5 seconds after establishing power supply. The pairing button is located on the circuit board on the back of the device.
Operating and alarm signals↑
|Description||Signal tone||Red LED|
|Normal operation||No sound||flashes every 40 seconds|
|Alarm state||Loud intermittent sound in 0.5 sec. intervals||2 flashes per second|
|Malfunction / Contamination||3 short beeps every 40 seconds||LED off|
|Low battery indicator||Short beep every 40 seconds||flashes every 40 seconds simultaneously with the signal tone|
|Alarm muting||No sound||flashes every 10 seconds|
|Alarm Memory active Alarm was active within the last 24h||No sound||flashes 3 times every 43 seconds|
|Functional test||Loud intermittent sound||flashes twice every second as long as the light guide button is pressed|
|Pairing mode||No sound||flashes every second|
|Alarm||Input is active when smoke is detected||0/1|
|Online Status Smoke Detector Air||Digital||0/1|
|Battery level||Provides the current battery level.||%||0...100|
|Battery low||Indicates low battery, battery needs to be replaced.||-||0/1|
|Monitor Online Status||You will be notified via System Status or Could Mailer if the device is no longer available or offline.
As this device and it's functionality are critical to safety, it is not possible to disable this setting for this device.
|Serial Number||Serial number of the Air device||-|
|Device type||Air device type||-|
|Start Value ON||When checked, the digital input value will be ON when starting the program.||-|
|Display Error Output||Error output will be displayed in 2nd row when ticked.||-|
|Smoke detectors should be checked once a year.|
Remove dust and insects from the smoke detector grille if necessary. Any smoke that may occur must be able to enter the smoke detector unhindered.
The smoke detector has a button for test purposes. Press the light guide button on the top until the smoke detector sounds the audible alarm. Please do not forget to activate the alarm suppression before doing so.