The Sauna Controller block allows you to control and monitor your sauna. All conventional heaters are compatible (switched heaters and heaters that accept a 0-10V control signal).
The function block has a timer function, fan and drying control, as well as a safety shut down in case you forget to switch off the heater. You can also use door contacts with the sauna to alert you if the door has been left open and is wasting heat and energy!
The function block can also be used in the user interface, for control whilst on the move! It is important that when using this block that you observe the safety regulations of your country.
Make sure to select appropriate sensors for the heat in the sauna!
See here our sauna temperature sensor in the webshop.
An over temperature manual cutoff thermostat must also be installed!
Connect the temperature sensor for the sauna to the input AI.
The outputs are for the various types of heaters, AQ for 0-10V analogue, Q1, Q2 and Q3 for stage L1, L2 and L3 heaters. If the heater is a single phase using Q1 we need to set the parameter M to 1.
Then connect the fan to the output Qf.
|T||Analogue input for desired target temperature|
|AI||Analogue temperature for actual temperature|
|Tc||Starts the hourglass timer|
|D||Door position sensor|
|P||Input for presence detector|
|AQ||Analogue output||0-10V control|
|Q1||Digital output||For turning Phase 1 (L1) on/off|
|Q2||Digital output||For turning Phase 2 (L2) on/off|
|Q3||Digital output||For turning Phase 3 (L3) on/off|
|Qa||Status output||For whether the sauna is active or not|
|Qf||Digital output for fan control|
|AQt||Remaining time for hourglass timer||[s]|
|Qd||Digital output status for airing phase|
|AQs||Status output for target temperature|
|Qte||Pulse when timer countdown finishes||Pulses when actual temperature is higher than desired temperature, see parameter Ts|
|Qta||Digital output||Gives the timer’s status (on/off)|
|Tc||Temperature correction||Adjustment for the actual temperature in the seating position (use if no bench sensor present)|
|Tn||Fan duration after airing time finished|
|Tt||Duration of hourglass timer|
|To||Maximum allowed temperature before a safety shutdown|
|Ts||Time before a safety shutdown occurs|
|M||Type of AC input used||Off = Three-phase
On = Single-phase