The Room Comfort Sensor Air is used to measure temperature and humidity in rooms or similar applications. The openings in the housing ensure rapid response to changes in temperature or humidity.
Table of Contents
The recommended mounting height for the indoor climate sensor is between 1.2 m (4 ft) - 1.5 m (5 ft) when mounted on the wall. The positioning of the sensor should be adapted to the application. (e.g. according to what area of a space is generally occupied)
Install the mounting frame at the desired location and connect the power supply (orange/white terminal). When using batteries, remove the orange/white terminal and insert the supplied AAA batteries.
The sensor is then snapped into the mounting frame. For free-standing use, install the supplied back cover instead of the mounting frame.
In delivery state, pairing mode will be active after the power supply has been established. This is indicated by the status LED flashing red/green/orange.
To activate the pairing mode manually, hold down the pairing button for at least 5 seconds after establishing power supply.
|Temperature||Provides the measured value of the current temperature||°||-40...125|
|Air humidity||Provides the measured value of the current air humidity||%||0...100|
|Online Status Room Comfort Sensor Air||Digital||-|
|Battery Low||This sensor switches on when the batteries are at a low state of charge.
The device only supplies values to this sensor when it is powered by batteries.
|Battery Level||This sensor indicates the current battery level.
If the device is externally supplied with 24v, the value of 100 is constantly shown.
|Summary||Description||Unit||Value Range||Default Value|
|Monitor online status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-||-||-|
|Air serial number||Serial number of the Air device||-||-||-|
|Device type||Air device type||-||-||-|
|Transmit cycle [min]||Request or transmit cycle for temperature and humidity (1-120 min, 0 = Off)||min||0...120||-|
When connecting to an external power supply, the installation must be carried out by a qualified technician in accordance with all applicable regulations.
The installation requires a suitable enclosure to ensure protection against contact, water and dust.
The device must not be used as part of safety-critical systems.