- Power supply: 24VDC
- Power rating (across all 4 channels evenly split)
- 100W @ 12VDC
- 200W @ 24VDC
- Outputs may be bridged
- Consumption: <150mW
- Maximum total power loss: 2.7W
- Control over Loxone Tree
- Operating temperature: 0°C – 55°C
- PWM Frequency: 123 Hz
- Max. Cable length to LED strip: <30m
- Dimensions: 34 x 85 x 49 mm (2 breaker units)
The status LED flashes orange initially on power-up. After the dimmer has been learnt in, the LED flashes briefly green for confirmation, then both LEDs are permanently off.
If the LED flashes red, check the wiring. Details for analysis can be found here .
Once the dimmer is listed in the peripheral screen. Drag and drop the dimming outputs to the configuration page.
If “Individual dimming channels” is selected as PWM configuration in the properties of the device, the channel assignment is as follows:
Red -> Dimmer 1
Green -> Dimmer 2
Blue -> Dimmer 3
White -> Dimmer 4
Wiring of RGBW spots
Wiring of WW spots
To identify the dimmer in the cabinet, click the dimmer in the periphery in Loxone config. The status LED on the RGBW Dimmer will then flash quickly alternately red green. If a channel of the dimmer is selected, this fades up and down and is thus clearly identifiable. The RGB output fades first red, second green and blue third.
The PWM dimmer should be placed as close as possible to the LED strip. The cross-section of the 24V voltage supply should be such that the voltage drop is a maximum of 1V.
The voltage drop can be calculated using the following formula:
ΔU = I · R = I · ((2 · L · ρ) / A)
I … Current [A]
L … Cable Length [m]
A … Cable Cross-Section [mm²]
ΔU … Voltage Drop [V]
ρ … Material Specific Resistance [( Ω*mm²)/m]
ρ= 0.0172 (for Copper)