This meter is suitable for recording consumption or delivery of various utilities such as electricity, gas, water, heat, etc.
For this purpose, the pulses of a physical meter with pulse output (S0) are read.
Together with other meter function blocks, various consumers, producers or storage units in the building can be linked via the Energy Flow Monitor for an overall display.
Table of Contents
|P||Pulse||For meters with pulse output (S0), connected to digital inputs.||0/1|
|F||Frequency||For meters with pulse output (S0), connected to digital inputs used as frequency counter.||0...∞|
|R||Reset||Pulse: Meter reading outputs are reset.
On: Block is locked.
|Pf||Power or flow||Power or flow rate
Calculated from pulse to pulse time and parameter Np.
Pulse interval <= 10 seconds: Updated and calculated by each pulse.
Pulse interval > 10 seconds: Update every 10 seconds, calculation of an average value.
|Rm||Reading this month||0...∞|
|Ry||Reading this year||0...∞|
|AC||API Connector||Intelligent API based connector.
|Abbreviation||Summary||Description||Value Range||Default Value|
|Np||Number of pulses per unit||0...∞||1000|
|Mro||Meter reading offset||Value is added to output (Mr).||∞||0|