This bidirectional meter is suitable for recording consumption and delivery of various utilities such as electricity, gas, water, heat, etc.
For this purpose, the pulses of a physical meter with pulse output (S0) are read.
Together with other meter function blocks, various consumers, producers or storage units in the building can be linked via the Energy Flow Monitor for an overall display.
Table of Contents
|Pc||Pulse consumption||For meters with pulse output (S0), connected to digital inputs.||0/1|
|Pd||Pulse delivery||For meters with pulse output (S0), connected to digital inputs.||0/1|
|Fc||Frequency consumption||For meters with pulse output (S0), connected to digital inputs used as frequency counter.||0...∞|
|Fd||Frequency delivery||For meters with pulse output (S0), connected to digital inputs used as frequency counter.||0...∞|
|R||Reset||Pulse: Meter reading outputs are reset.
On: Block is locked.
|Pf||Power or flow||Current power/flow calculated using inputs (Pc) and (Fc) is output as a positive value.
Current power/flow calculated using inputs (Pd) and (Fd) is output as a negative value.
|Mrc||Meter Reading consumption||0...∞|
|Rdc||Reading today consumption||0...∞|
|Rmc||Reading this month consumption||0...∞|
|Ryc||Reading this year consumption||0...∞|
|Mrd||Meter Reading delivery||0...∞|
|Rdd||Reading today delivery||0...∞|
|Rmd||Reading this month delivery||0...∞|
|Ryd||Reading this year delivery||0...∞|
|AC||API Connector||Intelligent API based connector.||-|
|Abbreviation||Summary||Description||Value Range||Default Value|
|Npc||Number of pulses per unit||0...∞||1000|
|Npd||Number of pulses per unit||0...∞||1000|
|Mroc||Meter reading offset consumption||Value is added to output (Mrc).||∞||0|
|Mrod||Meter reading offset delivery||Value is added to output (Mrd).||∞||0|