The Loxone Motion Detector Tree is used to detect motion and brightness in a room.
Note: The Motion Sensor Tree is no longer available and has been replaced by the Presence Sensor Tree.
|The Motion Sensor can also detect some pets. Although the sensitivity of the sensor can be reduced, there is no dedicated technology that excludes the detection of pets.|
Table of Contents
|For motion to be detected accurately, correct placement of the Motion Sensor on the ceiling is essential. The following drawings can assist with this:|
Connect the power supply (orange/white terminal) and Tree communication wires (green/white terminals). To complete the installation, attach the Presence Sensor to the mounting ring. Shortly after power-up, the status LED will blink orange if the wiring is correct (connection to Tree Extension and Miniserver is established).
|Motion||Input is active when motion is detected||-||0/1|
|Brightness||Provides the measured value of the current brightness||Lx||0...188|
|Online Status Motion Sensor Tree||Digital||0/1|
|Summary||Description||Unit||Value Range||Default Value|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-||-||-|
|Serial Number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Device type||Tree device type||-||-||-|
|Sensitivity||Effects the sensitivity and thus also the distance over which motion can be sensed||-||-||-|
|Overrun Duration Following Motion||The 'Motion (Mv)' input remains active following the last detected motion for the set time. A higher value means less packets have to be sent via Tree and Link.
If the motion detector is used for the alarm system, the time is automatically set to 3 seconds when the alarm system is armed.
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.