The Loxone Motion Detector Air is used to detect motion and brightness in a room. It can be operated either by battery or external power supply.
Note: The Motion Sensor Air is no longer available and has been replaced by the Presence Sensor Air.
|The Motion Sensor can also detect some pets. Although the sensitivity of the sensor can be reduced, there is no dedicated technology that excludes the detection of pets.|
Table of Contents
- Battery Replacement
- Inputs, Outputs, Properties
- Safety Instructions
|For motion to be detected accurately, correct placement of the Motion Sensor on the ceiling is essential. The following drawings can assist with this:|
Install the mounting ring at the desired location. Insert the batteries or connect the 24VDC power supply. To complete the installation, attach the Motion Sensor to the mounting ring.
In delivery state, pairing mode will be active after inserting the battery or after the power supply has been established. This is indicated by the status LED flashing red/green/orange.
To activate the pairing mode manually, hold down the pairing button for at least 5 seconds after establishing power supply. The pairing button is located on the back of the device.
The available functions differ depending on whether the device is battery operated or connected to an external power supply. This is determined during pairing. The device must therefore be paired in the same supply method in which it is to be operated later.
If the supply method is changed later, the device must be deleted from the configuration and paired again.
To replace the batteries, remove the unit from its base by briefly turning it anticlockwise. Remove the batteries from the back of the unit and insert new AA batteries. The device will restart and the status LED will flash green 3 times.
|Motion||Input is active when motion is detected||-||0/1|
|Brightness||Provides the measured value of the current brightness||Lx||0...188|
|Online Status Motion Sensor Air||Digital||0/1|
|Battery level||Provides the current battery level.||%||0...100|
|Battery low||Indicates low battery, battery needs to be replaced.||-||0/1|
|Summary||Description||Unit||Value Range||Default Value|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-||-||-|
|Air serial number||Serial number of the Air device||-||-||-|
|Device type||Air device type||-||-||-|
|Brightness Transmission Cycle||Brightness transmission cycle (0=OFF).||min||0...120||-|
|Overrun Duration Following Motion||The 'Motion' input (Mv) will remain ON for this duration after detecting the last movement. The longer this overrun period, the more energy efficient the device can operate.
If a motion sensor is used as part of a burglar alarm, then the overrun period will automatically be set to 3 seconds when the alarm is armed and the device reports to the Miniserver.
|Sensitivity||Effects the sensitivity and thus also the distance over which motion can be sensed||-||-||-|
When connecting to an external power supply, the installation must be carried out by a qualified technician in accordance with all applicable regulations.
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.