The Loxone LED Ceiling Spot WW Tree provides warm white light. It is controlled and dimmed directly via the Tree interface.
Table of Contents
Switch off the supply voltage before installation.
Mount the base plate to the ceiling. The spot will be held to the base plate by 2 magnets.
Connect the power supply and Tree communication wires.
Then place the lamp on the base plate. Make sure that the magnets are positioned correctly and that no wires are jammed.
The additional safety rope is a security feature and must not be removed!
For lights, a commissioning mode is active when the devices are supplied with power and have not yet been paired.
In this mode, the device indicates whether it has been connected correctly and, if the connection is successful, provides lighting until it has been paired.
This function is supported since Loxone Config 184.108.40.206, depending on the device firmware.
|Smart Actuator WW||Smart actuator||∞|
|Online Status LED Ceiling Spot WW Tree||Digital||0/1|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-|
|Serial Number||Specifies the serial number of the device.
For Extensions: Enter 'Auto' to automatically pair an extension with unknown serial number.
This can only be used if there is only one Extension of the same type.
Save into the Miniserver, in order to pair the Extension.
Afterwards the program must be loaded from the Miniserver to transfer the actual serial number of the Extension into the program.
|Device type||Tree device type||-|
|Actuator Type||Use device with Standard Actuator(s) or Smart Actuator(s)
Smart Actuators support dynamic fade times and can only be used with the Lighting Controller.
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.