The Loxone LED Ceiling Light RGBW Tree is a surface mounted 24VDC fixture with warm white and coloured light. It features an integrated motion and brightness sensor. It is connected to the Miniserver via the Loxone Tree technology.
Table of Contents
Switch off the supply voltage before installation.
Mount the base plate to the ceiling. The lamp will be held to the base plate by 3 magnets.
Connect the power supply and Tree communication wires.
Then place the lamp on the base plate. Make sure that the magnets are positioned correctly and that no wires are jammed.
The additional safety rope is a security feature and must not be removed!
Shortly after power-up, the status LED will blink orange if the wiring is correct (connection to Tree Extension and Miniserver is established).
|Motion||Input is active when motion is detected||-||0/1|
|Brightness||Provides the measured value of the current brightness||Lx||∞|
|Online Status LED Ceiling Light RGBW Tree||Digital||0/1|
|Summary||Description||Unit||Value Range||Default Value|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-||-||-|
|Serial Number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Device type||Tree device type||-||-||-|
|Actuator Type||Use device with Standard Actuator(s) or Smart Actuator(s)
Smart Actuators support dynamic fade times and can only be used with the Lighting Controller.
|Sensitivity||Effects the sensitivity and thus also the distance over which motion can be sensed||-||-||-|
|Overrun Duration Following Motion||The 'Motion (Mv)' input remains active following the last detected motion for the set time. A higher value means less packets have to be sent via Tree and Link.
If the motion detector is used for the alarm system, the time is automatically set to 3 seconds when the alarm system is armed.
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.