The Loxone LED Ceiling Light RGBW Air is a surface mounted fixture with warm white and coloured light. It features an integrated motion and brightness sensor. It is connected to the Miniserver via the Loxone Air wireless technology.
Table of Contents
Switch off the supply voltage before installation.
Mount the base plate to the ceiling. The lamp will be held to the base plate by 3 magnets.
Connect the mains voltage lines (L, N, PE).
Then place the lamp on the base plate. Make sure that the magnets are positioned correctly and that no wires are jammed.
The additional safety rope is a security feature and must not be removed!
In delivery state, pairing mode will be active after the power supply has been established. This is indicated by the status LED flashing red/green/orange.
To activate the pairing mode manually, switch off the power for 10 seconds, then switch it back on. If no connection to a Miniserver can be established for two minutes, then pairing mode is activated for 30 minutes.
|Motion||Input is active when motion is detected||-||0/1|
|Brightness||Provides the measured value of the current brightness||Lx||∞|
|Smart Actuator||The minimum fading time is 1s.||∞|
|Online Status LED Ceiling Light RGBW Air||Digital||0/1|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-|
|Serial Number||Serial number of Air device||-|
|Device type||Air device type||-|
|Actuator Type||Use device with Standard Actuator(s) or Smart Actuator(s)
Smart Actuators support dynamic fade times and can only be used with the Lighting Controller.
|Overrun Duration Following Motion||The 'Motion' input (Mo) will remain ON for this duration after detecting the last movement. The longer this overrun period, the more energy efficient the device can operate.
If a motion sensor is used as part of a burglar alarm, then the overrun period will automatically be set to 3 seconds when the alarm is armed and the device reports to the Miniserver.
|Sensitivity||Effects the sensitivity and thus also the distance over which motion can be sensed||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
Ensure that the device is protected from water.
The device must not be used as part of safety-critical systems.