The Leaf Tree is a decentralized ventilation unit with heat recovery that is controlled via Loxone Tree technology. Several units are combined, providing room ventilation. More information about the operating method and a configuration tool for the recommended number of units can be found on the website of our cooperation partner: Leaf Ventilation.
Table of Contents
- Maintenance, filter replacement
- Inputs, Outputs, Properties
- Safety Instructions
Connect the 24V DC power supply and Tree communication wires. Shortly after power-up, the status LED will blink orange if the wiring is correct (connection to Tree Extension and Miniserver is established).
Maintenance, filter replacement↑
The fan filter must be replaced or cleaned at regular intervals based on the maintenance manual. The filter change interval can be defined in the Leaf 1 properties. This setting is 3 months (2200h) by default. The actual run-time of the fan is considered. You will be notified of an upcoming maintenance in the user interface.
|Online Status Leaf Tree||Digital|
|Monitor online status||When selected, you will be notified via System Status or the Cloud Mailer if the device is no longer available or goes offline.||-|
|Serial number||Specifies the serial number of the device.
For Extensions: 'Auto' may only be used if only one Extension of this type is being used.
|Device type||Tree device type||-|
|Filter Change Interval||After this time (in hours) the filter warning becomes active.||2200|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The device must not be used as part of safety-critical systems.
Please note the safety instructions in the following installation and operating manual.