The Leaf Air is a decentralized ventilation unit with heat recovery that is controlled via Loxone Air technology. Several units are combined, providing room ventilation. More information about the operating method and a configuration tool for the recommended number of units can be found on the website of our cooperation partner: Leaf Ventilation.
Table of Contents
- Maintenance, filter replacement
- Inputs, Outputs, Properties
- Safety Instructions
In delivery state, pairing mode will be active after the power supply has been established. This is indicated by the status LED flashing red/green/orange.
To activate the pairing mode manually, switch off the power for 10 seconds, then switch it back on. If no connection to a Miniserver can be established for two minutes, then pairing mode is activated for 30 minutes.
Maintenance, filter replacement↑
The fan filter must be replaced or cleaned at regular intervals based on the maintenance manual. The filter change interval can be defined in the Leaf 1 properties. This setting is 3 months (2200h) by default. The actual run-time of the fan is considered. You will be notified of an upcoming maintenance in the user interface.
|Online Status Leaf Air||Digital||0/1|
|Summary||Description||Value Range||Default Value|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-||-|
|Serial Number||Serial number of the Air device||-||-|
|Device type||Air device type||-||-|
|Filter Change Interval||After this time (in hours) the filter warning becomes active.||∞||-|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The device must not be used as part of safety-critical systems.
Please note the safety instructions in the following installation and operating manual.