How to setup your Damper Tree.
- Power supply: 15 … 30 VDC SELV
- Pipe Diameter: 6”, 7”, 8”, 10” available, other sizes on request
- Operating temperature: 0…55°C / 32…131°F
- Humidity: 80% RH
- Maximum power consumption: 0.2W, max. 2.3W (when motor is driving)
- Protection: IP20
- No maintenance required.
- Cable Diameter: 0.258 – 0.34 mm²
- Connection Wire Diameter: 0.25…0.8mm² / AWG18…AWG23 Exposed Wire Length: 5mm / 13/64”
ABOUT THE PRODUCT
By integrating the Damper Tree you can connect your HVAC System to your Loxone Miniserver. Get a fully-fledged self-learning and easy to use heating and cooling control. It gives you the perfect temperature throughout the day – while keeping the energy bills low.
The installation of this device must be carried out by a qualified individual. When installed, the device must follow building regulations for electrical and fire safety. If the device is not installed according to manufacturer’s guidelines, the warranty of the device may be affected. Install the damper between the ventilation ducts and fix them with a foil tape that is certified to in that kind of installation. Connect SELV and Tree communication to the Damper Tree. Once connected power up the device and configure it using our simple to use Loxone Config.
The Damper Tree performs calibration after being learned into the system.
To commission, the damper tree connects the 24V power (orange/orange-white) and the Tree (green/green-white).
There are also the following outputs for troubleshooting:
- Online Status
- Damper stuck
The analog output of the actuator can be linked directly to the out put ‘AQh & ACc’ of the HVAC Room controller block. The HVAC Room controller block is not available in the official release at the moment. Please get in touch with us if you would like to get the beta version of our function block. ([email protected]).
Please note the LED’s on the Damper Tree cannot be disabled.
|RED flashing quickly (approx 5Hz)||no bus communication possible|
Please check cabling
|YELLOW flashing quickly|
|Tree device was detected on the bus, but it is not learnt in the Miniserver|
|GREEN 3x short flashes||Device learned in, communication OK|
|Online, Damper >75% open|
|Online, Damper between 25% -75%|
|Online, Damper < 25% open|
|RED light||There is the problem with the Damper, please check if the damper is free to move|
The Damper can open or close completely for test purposes. To perform this test, right click on the Damper in the Periphery. Here, you can now carry out the device Start Device Test (= fully open Damper), Stop Device Test (= fully close Damper) and obtain the travel details (Re-calibrate Device).
To ensure that the Damper knows the exact movement they must run a calibration procedure. This is done automatically when you first learn the Damper in so we recommend you learn in and power up your Damper for the first time once installed.