DALI Air is a compact Interface to wirelessly integrate up to 10 DALI devices, either in broadcast mode or by assigning dedicated addresses. It is DALI-2 certified and supports also DALI Sensors.
Table of Contents
- Pairing DALI Devices
- DALI Broadcast
- Inputs, Outputs, Properties
- Safety Instructions
Install the device in a suitable installation box.
Connect the AC mains supply (brown/blue wire), as well as the DALI data lines (grey screw terminal).
In delivery state, pairing mode will be active after the power supply has been established. This is indicated by the status LED flashing red/green/orange.
To activate the pairing mode manually, switch off the power for 10 seconds, then switch it back on. If no connection to a Miniserver can be established for two minutes, then pairing mode is activated for 30 minutes.
Pairing DALI Devices↑
To search for DALI devices, first click on the DALI Air in Loxone Config, and then activate DALI search:
It will then search for devices and display the discovered devices. By clicking the right arrow, selected devices are added to the programming.
After that, the added devices are available in the periphery tree, and can be used on the programming page:
Using a DALI broadcast, you can effortlessly control all compatible DALI bus devices at once, without the need for individual pairing or programming. To enable this feature, simply activate the Broadcast Application in the DALI Air settings.
|Online Status Dali Extension Air||Digital||0/1|
|Monitor Online Status||When selected, you will be notified via System Status or the Mailer if the device is no longer available or goes offline.||-|
|Serial Number||Serial number of Air device||-|
|Device type||Air device type||-|
Installation must be carried out by a qualified electrician in accordance with the applicable regulations.
This device must be mounted in an electrical enclosure to ensure protection against contact, water and dust.
This device must not be used as part of safety-critical systems.