The Alarm Siren Air is an external warning device with strobe light, for example as part of the burglar alarm. When triggered, the device emits an audible and visual alarm. The integrated tamper switch provides additional protection.
Table of Contents
Select an installation location where the device is protected from extreme weather conditions and damage. Make sure that the cable outlet is covered by the unit after installation.
Connect the power supply (orange/white) using the supplied 3M jelly crimp connectors. The wires including insulation are inserted into the connector, then the connector is crimped with pliers.
To complete the installation, place the top cover on the base unit and secure it to the bottom with the two screws.
In delivery state, pairing mode will be active after the power supply has been established. This is indicated by the status LED flashing red/green/orange.
To activate the pairing mode manually, switch off the power for 10 seconds, then switch it back on. If no connection to a Miniserver can be established for two minutes, then pairing mode is activated. The device can then be paired again.
|Tamper switch||Input is active in normal state. The input is deactivated when sabotage is detected by the contact on the device.|
|Alarm light||Output to activate the alarm light|
|Alarm sound||Output to activate the alarm sound|
|Online Status Alarm Siren Air||Digital|
|Summary||Description||Unit||Value Range||Default Value|
|Monitor Online Status||You will be notified via System Status or Could Mailer if the device is no longer available or offline.
As this device and it's functionality are critical to safety, it is not possible to disable this setting for this device.
|Air serial number||Serial number of the Air device||-||-||-|
|Device type||Air device type||-||-||-|
|Maximum audible alarm duration [s]||Maximum audible alarm duration (0 - 1800 seconds, 0 = no limit)||s||0...1800||120|
The installation must be carried out by a qualified technician in accordance with all applicable regulations.
The device must not be used as part of safety-critical systems.