Quick Start Guide
|Room Comfort Sensor Air||Room Climate Sensor Air – Battery Operated||Room Comfort Sensor Tree|
|Power Supply||9…28VDC SELV||2x AAA Batteries||9…28VDC SELV|
|Power Consumption||typ. 65mW|
|Battery Life||/||Approx. 2 Years||/|
|Cleaning||No Maintenance Required. Clean with a damp cloth.|
|Dimensions||55x55x18mm without Frame. 80x80x18mm with Frame|
|Temperature||-40…125°C +/- 0.5ºC|
|Humidity||0…100% r.H. (Non Condensing) +/- 2%|
|CO²||No C0² Sensor||400…10,000ppm|
|Room Climate Sensor Air||Room Climate Sensor Tree|
|The Room Climate Sensor Air can be supplied with two AAA batteries or a fixed power supply of 9…28VDC.||To pair the Room Climate Sensor Tree, connect the power supply (Orange/White Terminals) and the Tree cables (Green/White Terminals). We recommend the Loxone Tree Cable for wiring the Room Comfort Sensor Tree.|
|The recommended mounting height for the Room Comfort Sensor is between 1.2m – 1.5m when mounted on the wall. It is important that the sensors are positioned correctly in order to allow accurate control of the Room Climate. The positioning of the sensor should therefore be adapted to the conditions of the room (e.g. according to where people in the room normally are).|
|The Room Comfort Sensor Air can also be freely placed on suitable surfaces when in battery operation, using the supplied cover. (e.g. on tables, on shelves, etc.)||The Room Comfort Sensor is wall mounted using the supplied mounting frame. For this purpose, the frame is mounted on an installation box or a suitable surface and the Room Comfort Sensor can then simply be snapped into the frame.|
For a detailed description of how to pair Tree devices, see here.
For a detailed description of how to pair Air devices, see here.