Smart Socket Air Setup
How to setup your Smart Socket Air.
- Suitable for a voltage of 85 - 265VAC
- Max. switching capacity: 13A
- Integrated measurement of energy (kWh), power (kW) and temperature (-20 to 50°C)
- Frequency: 868MHz
- Power consumption: <500mW
- Protection: IP20
Transfer of energy and power:
Every 5 minutes information about the energy and power is sent to the Miniserver.
If a 5% change in the data occurs this update is sent immediately to the Miniserver.
Transmission of the temperature:
Every 5 minutes the temperature is sent to the Miniserver.
USA, Turkmenistan, Trinidad, Tobago, Thailand, Thaiti, Saudi Arabia, Puerto Rico, Peru, Paraguay, Panama, Okinawa, Niger, Netherlands Antilles, Montserrat, Micronesia, Liberia, Lebanon, Colombia, Canada, Cayman Islands, Virgin Islands, Japan, Jamaica, Honduras, Haiti, Guyana, Guatemala, Guam, Ecuador, Dominican Republic, Costa Rica, Brazil, Bermuda, Barbados, Aruba, Barbuda, Venezuela.
France, Belgium, Monaco, Czech Republic, Slovakia, Tunisia, many former French colonies.
United Kingdom, Bahrain, Bangladesh, Belize, Bhutan, Botswana, Brunei, Dominica, El Salvador, Falkland Islands, Gambia, Guatemala, Guyana, Hong Kong, Ireland, Isle of Man, Yemen, Cambodia, Channel Islands, Qatar, Kenya, Kuwait, Lebanon, Macau , Malawi, Malaysia, Maledicen, Malta, Mauritius, Myanmar, Nigeria, Oman, Zambia, Seychelles, Tanzania, Cyprus, Singapore.
Switzerland, Liechtenstein, Maldives, Madagascar, Rwanda, Ethiopia, El Salvador, Jordan.
Afghanistan, Algeria, Andorra, Bosnia and Herzegovina, Bulgaria, Germany, Estonia, Finland, Greece, Indonesia, Iceland, Italy / San Marino / Vatican City, Korea, Croatia, Latvia, Lithuania, Luxembourg, Macedonia, Montenegro, Moldova, Netherlands, Norway , Austria, Portugal, Romania, Russia, Sweden, Serbia, Slovenia, Spain, South Korea, Syria, Turkey, Ukraine, Hungary.
Setup in Loxone Config
Plug in your Smart Socket and then open up Loxone Config. In order to learn in the Smart Socket you need to activate the Air Monitor. Click on the Air Base extension in the periphery window and then in the context bar at the top check the tick box 'Air Monitor'.
Now press and hold the learn button for 5 seconds on the Smart Socket - see the picture below.
When the program button is held for 5 seconds the Smart Socket sends a signal which can be seen in the Air Monitor. A short press works as a digital input.
Switch the Air Monitor to the learn mode and click on the correct Smart Socket signal. Enter a name for this Smart Socket and then click 'Create device'. The Smart Socket can now be seen in the periphery tree underneath the Air Base Extension.
The Air devices will run their update automatically in the background, and they will function throughout the update.
If the Air devices are updating when the Miniserver and the Air Base Extension are rebooted then the Air devices will restart the update from the beginning after the reboot.
The update can take up to an hour so do be aware of this! You can check the version of the devices by looking in Device status. Click on the Miniserver tab and then click the Device status button once.
|Flashing yellow||Haven't yet been paired with the Air Base|
|Flashing red||No connection to the Air Base possible|
|Flashes green for 3 secs||After being restarted a connection to the Air Base was successful|
|No LED||Device operational|
You can connect the energy and power inputs of the Smart Socket Air to an Electricity meter function block to display things like Today's usage, This Month's usage etc. You can also simply tick 'Use' on the inputs in the properties to show the current energy and power readings.